300 KW Biogas Generator
Ratings *Ratings at 0.8 power factor Performance Data * The above fuel consumption is calculate with the natural gas whose heat value is 35.8MJ/Nm 3 Dimensions and Weights Engine Brand & Model: HGKT38 Engine Data Gen-set Fastening and Shock-proof Devices: In general when manufacturing, a...
50Hz, 380/220V, 3 phases and 4 wires
*Ratings at 0.8 power factor
Engine Brand & Model
Alternator Brand & Model
Standard Noise Level@7m (Soundproof Sets)
Circuit Breaker Type
3 Poles MCCB
Frequency & Phase
50hz 3Phases + 4Wires
Engine Speed (RPM)
Fuel Consumption (Nm3/hr) 100% Load
* The above fuel consumption is calculate with the natural gas whose heat value is 35.8MJ/Nm3
Dimensions and Weights
Engine Brand & Model: HGKT38
No. of Cylinders
12 V Type
Bore * Stroke (mm)
159 * 159
Turbocharged & Aftercooled
24V DC motor
Coolant capacity, including radiator (L)
15W40-CF4 or above grade
Oil pan capacity (L)
Gen-set Fastening and Shock-proof Devices:
In general when manufacturing, a Cushioning Pad has been installed on the rigid base of the generator set, and has proofread the engine and the alternator exactly. So only need to install the genset in a predetermined position, and put in standard level.
If the genset is not installed with shockproof pad, shockproof device will be needed when the genset is placed on the flat-panel; rubber cushion or steel shells can be used to decrease vibration, otherwise the genset will be damaged or have unsuitable shock.
If possible, the concrete foundation should tamp the below raw soil or backfilling concrete in advance, then form a 200mm layer of shock absorption with cement, asphalt, cinder mixed with water. It can prevent the shock of genset and the resonance of some of the plant.
WARNING: The inherent vibration rate should be more than two times of the engine speed. If it close to the engine speed, parts of the plant may have the possibility to make resonance.
The running of the engine and operation of the alternator will spread heat all through the plant room and raise the temperature of the room, so ventilation is essential. It can control the plant room temperature effectively, and supply the generator with cool and fresh air.
Noise level is decided by the size of power room and level of noise pressure.Reduce the noise to the level corresponding to the environmental noise standard. No need to excessive demands, because this will cause unnecessary high cost.
For many installation, use flexible frame to fix genset, plus the normal control of air exhaust, air inlet and radiator fan, which can reduce the noise to an acceptable level.
If the noise remain high after these processing, we can set sound insulation board in the room or around the gensets. Fix sound-absorbing board on the wall of the room or put the genset in a special designed sound insulation container to reduce noise.