80 KW Gas Generator
Ratings *Ratings at 0.8 power factor Performance Data * The above fuel consumption is calculate with the natural gas whose heat value is 35.8MJ/Nm3 Dimensions and Weights Preparation before genset starting: Before genset starting, check and adjust the whole generator set to keep it in good...
50Hz,380/220V, 3 phases and 4 wires
*Ratings at 0.8 power factor
Engine Brand & Model
Alternator Brand & Model
Standard Noise Level@7m (Soundproof Sets)
Circuit Breaker Type
3 Poles MCCB
Frequency & Phase
50hz 3Phases + 4Wires
Engine Speed (RPM)
Fuel Consumption (Nm3/hr) 100% Load
* The above fuel consumption is calculate with the natural gas whose heat value is 35.8MJ/Nm3
Dimensions and Weights
Engine Brand & Model: HGT6B
No. of Cylinders
Bore * Stroke (mm)
Turbocharged & Aftercooled
24V DC motor
Coolant capacity, including radiator (L)
15W40-CF4 or above grade
Oil pan capacity (L)
Preparation before genset starting:
Before genset starting, check and adjust the whole generator set to keep it in good condition. The connection and fixing of every module must be liable, as well as the gneset's cooling system and electrical starting system to ensure no leaking, no loosing, flexible transfer switch, good lubrication. Gas supply system should be normal, otherwise you have to mend it at once or re-adjust it correctly and then restart it.
All CAMDA supplying gas gensets have been finished the testing. So it can be used with load directly. When it is used for the first time, CAMDA advice its load better to be 80%-90% of full load. When it is for continous usage, please ensure its load to be 75%-80% of full load.
◇clean the dust, water track, oil stain and rust on genset.
◇check whether all connecting parts and fastening pieces are loose or not; check all moving parts are flexible or not. Is there any part jammed? Check all connecting wires are correct and firm.Check if there is any wire drop off or loosen.
◇Check whether gas intake pipe unobstructed or not.
◇Turn on gas intake pipe switch.
◇Check whether there is enough oil in oil pan.
◇Whether the cooler is full of coolant or not.
◇Put all the switches on corresponding working position, the air breaker should be placed at "off" position.