1, battery power shortage-check the battery charge.
2, battery line and plug loose-check and fastening the battery line and plug.
3, intermediate relay failure-check intermediate relay action is normal.
4, starter failure-overhaul starter.
5, oil supply system is not smooth, do not supply oil-exhaust fuel system in the air, dredge the pipeline so that fuel flow overhaul oil pump, cleaning the first filter.
6, start the button, the start loop contact bad-Replace the button, check the starting circuit.
7, spray nozzle oil-free injection (oil is not smooth)-check from the fuel tank to the oil pump between the circuit has no leakage, blockage.
8, the fuel system into the air--open the exhaust screws to check the oil situation.
9, injection pump fuel injection time is not accurate or fuel injection pump failure--the time to adjust fuel injection pump.
10, speed regulator operation handle position is not-start, the governor handle placed no-load position. 11, electric adjustment Board, actuator, speed sensor, such as circuit failure-check the corresponding equipment and circuit respectively.
Related Industry Knowledge
- Diesel Generator Set Model meaning
- Main uses of generator sets
- Performance grade of Diesel generator set
- Installation requirements for Diesel generator set
- Diesel Generator Set Purchase step
- Diesel Generator Set Replacement oil
- Common Unit Selection
- Noise treatment of diesel generating unit durin...
- How to check and accept diesel generating set a...
- How to judge whether a diesel generating set is...
- 24kW two-bearings diesel genset in Fiji
- Diesel Pump Genset, Singapore
- Standby 310kW diesel genset installed in Zhuhai
- Water pump sets powered by diesel engine in New...
- Biogas plant, Bangladesh