First, in the case of unit downtime, check the appearance of the unit, the instruments and meters, cable joints are intact, if found to have problems, you need to do the appropriate processing to accept;
Second, after the boot before the inspection, (including cooling water, fuel oil, waterway pipeline joints leakage, etc.) manual commissioning of the generator set, check the parameters of the unit is normal, and then downtime, and then do automatic debugging, check the parameters of the unit is normal;
Third, with load test, no-load test after the completion of the unit to do manual and automatic belt load test, please note that the operating procedures of the generator set, carefully check the output parameters of the generator set is normal, the sound is abnormal and so on.
Four, start the power supply part of the load, carefully check whether the load is running normally. Check whether the protection performance of the generator set is intact, safe and reliable.
Related Industry Knowledge
- Diesel Generator Set Model meaning
- Main uses of generator sets
- Performance grade of Diesel generator set
- Installation requirements for Diesel generator set
- Diesel Generator Set Purchase step
- Common failures of Diesel generator set
- Diesel Generator Set Replacement oil
- Common Unit Selection
- Noise treatment of diesel generating unit durin...
- How to judge whether a diesel generating set is...
- 24kW two-bearings diesel genset in Fiji
- Diesel Pump Genset, Singapore
- Standby 310kW diesel genset installed in Zhuhai
- Water pump sets powered by diesel engine in New...
- Biogas plant, Bangladesh
- Biogas plant, Sweden
- Biogas Plant in Czech
- Biogas plant in Thailand
- Biogas plant Selangor, Malaysia